Fuel Sampling and Fixed Fuel Polisher Installation
Company FM Company Region London Sector Data Centre
Following the analysis of samples taken from the bulk tanks used to provide back-up fuel for a leading nance institutes data centre, it was decided that fuel required polishing to ensure the tanks were kept free of contamination. With this data centre home to such critical information, a xed, on-site fuel polishing machine was suggested to minimise the risk of future fuel contamination.
Adler and Allan installed a fixed polishing machine, into the existing fuel system. The polisher removes debris of up to two microns and metals, through a magnetic particle filter and water separator. The polisher has been set up to automatically run every day for four hours, circulating the fuel and removing any contaminants.
With the new polisher installed, the risk of future fuel contamination is substantially lowered, ensuring the smooth operation of the crucial commerce centre.
PDF version available here